BayEnergy® Power cables, PVC insulation, PE sheath
4-cores acc. to DIN VDE 0276 part 603
DIN VDE 0276-603 part 3G / HD 603.1 and IEC 60502-1.
The cables are in compliance with EU LVD (Low Voltage Directive 2014/35/EU) and RoHS Directive EU 2002/65/EC - RoHS 2.0 and Regulation No. 1907/2006 (REACH).
They are flame retardant and self-extinguishing according to DIN EN 50265-2-1 (IEC 60332-1-2) and free of silicone, cadmium and free from substances harmful to the wetting properties of lacquers.
|Rated voltage kV||0.6/1|
|Testing voltage kV||4|
Cable temperature ºC
during laying (min)
after laying (max)
-5 to +50
-30 to +70
|Max permissible operating temperature (conductor) °C||+70|
|Short-circuit temperature °C||+160|
For installation in open air, in the ground, for power stations, industry and distribution boards or subscriber networks, especially under extreme operation and temperature conditions. (See DIN VDE 0298-1.)
For indoor installation, taking into account that the PE sheath is halogen-free, however not flame retardant according DIN VDE 0472, part 804, test type B.
The cables are UV-resistant and particularly resistant due to the outer sheath made of HDPE.
Type Designation Codes
|N||cables acc. to standard|
|(N)||cables based on standard|
|A||conductor made of aluminium|
|Y||insulation made of polyvinyl chloride (PVC)|
|2Y||outer sheath made of high-density polyethylene (HDPE)|
|O||cable without green-yellow core|
|RE||circular conductor, solid|
|RM||circular conductor, stranded|
|SE||sector-shaped conductor, solid|
|SM||sector-shaped conductor, stranded|
Design according to national and international standards
Design according to customer specifications
Design with limited tolerance of outer diameter on request
NAY2Y-O 4x120 SE 0,6/1kV